Flooding System incorporating smoke detector
The fire alarm system is exclusively designed for multiple zone monitoring and control of allied operations as required for fire control operations.
The system is equipped with smoke detector, M.S. Seamless Piping, CO2 cylinder banks, Nozzles etc. etc. Smoke detectors are divided
in different zones for control room & server room.
The control panel continuously shows the status of each zone for following possibilities and gives Audio visual signal for status except
"GOOD" i.e. in normal working it will display "GOOD".
The power requirement is -230 volt A.C. + - 5% 50 cycles. In case of low/high voltage prevailing in the system, it is recommended to install
750 V.A. voltage stabilizers.
Any defective zone can be isolated from the system without effecting the working of other zones. This can be done by zonal switch provided with each zone.
Optional (If battery back up is provided) :
The panel is equipped with two wet chargeable batteries each of
In case of failure of the A.C. Mains the system automatically switches all functions to battery i.e. The system remains operative even if main power has failed. The batteries used in the system should be checked regularly and if required should be topped up with the electrolyte. Batteries are trickle charged from the charger in
corporate in the panel. If required same can be boost switch provided on panel.